Dynamic elaboration on the Art & Science of Hazardous Area Protection
Some Definitions to start with:–
From the Enchanting world of MUSIC:–
An overtone accompanying a fundamental tone at a fixed interval, produced by vibration of a string, column of air, etc. in an exact fraction of its length.
From the Mystical world of ASTROLOGY
A division of the zodiacal circle by a specified number, used in the interpretation of a birth chart.
From the logical & analytical world of PHYSICS
A component frequency of an oscillation or wave.
From the Interesting & my favorite world of Electrical Engineering
Harmonics are a distortion of the normal electrical current waveform, generally transmitted by nonlinear loads
Harmonics add richness , depth & everlasting magic to music . You can always go down the memory lane & time passages , accompanied by your favourite musical piece.
This sweet flavour of Harmonics in MUSIC becomes very bitter when added to Alternating Electrical Voltages & Currents with base frequency of 50 or 60 Hz.
At this point let us meet Jean-Baptiste Joseph Fourier (21 March 1768 – 16 May 1830)
He was a French mathematician and physicist born in Auxerre and best known for initiating the investigation of Fourier series and their applications to problems of heat transfer and vibrations. The Fourier transform and Fourier’s law are also named in his honour. (Wikipedia)
He invented Fourrier Series which led to Fourrier Analysis
by virtue of which general functions may be represented or approximated by sums of simpler trigonometric functions.
The figure shows the Fundamental wave and its multiples operating simultaneously.
The combined effect can be obtained by the simple processes of summation
The resultant wave is distorted due to the addition of waves of frequencies which are multiples of the main wave (fundamental) .
This distortion in Power Frequency voltage & resulting current wave is due to the non-linear nature of the catered load.
The bitterness of Harmonics is manifested in many ways . We will not go into details
The most obvious and harmful effect is the increase in operating temperature of the electrical equipment .
This harmful effect becomes DANGEROUS as it invalidates the designed TEMPERATURE CLASS of the operating equipment by bringing it down by 1 or 2 notches.
This may lead to all sorts of violations of the safety parameters and the safe operation of the equipment within the Hazardous Area becomes an uncertainty .
Harmonics in the power supply due to nonlinear loads will alter the T- Rating of all the equipment in that branch as far as the temperature class is concerned.
The harmonics ‘distort ‘ the temperature class, due to extra current (zero sequence) generated heat which is not anticipated in nonlinear-loaded networks.
The following parameter has to be taken in consideration when Electrical Equipment are selected for use in hazardous area.
TOTAL HARMONIC DISTORTION or (THD)
THD is a common measurement of the level of harmonic distortion present in power systems.
Within the same perspective the Power Factor has to be modified by considering THD.
Power factor is the ratio of kilowatts & kilo-Volt-Ampere (kW/kVA) . In reality it is the combination of Displacement Part & Distortion Part
In fact : Power Factor = Displacement part X Distortion part
= COSINE of phase angle between Voltage & Current X Ratio of rms value of Fundamental Frequency of Current & rms vale of the total current (rms : Root mean square )
= cos θ x rms I (fundamental-frequency) / rms I (total)
The distorted waveform of Current is due to the presence of capacitor as one circuit element .The above waveform is for the power supply as shown below .
IEC 61000-3-2 tabulates the power factor and /or THD requirements for Energy Star 80 Plus
(Source : https://www.allaboutcircuits.com/technical-articles …)